This is a solution of A/C for a UPS room. The characteristic of the UPS room is the workplace in back-up power facility, and there is a large amount of equipment. Personnel are not too much. According to the characteristics of the space for the UPS room, the selection of model is recommended as CB-V065.
The total area is of about 100 square meters for the UPS room, and there is a large amount of heat source (15KW), and it requires the temperature and humidity control and energy saving features. Required cooling capacity per square meter on average calculated based on the actual situation according to 400W, the total demand for cooling capacity is of 55KW.
To meet the cooling capacity of 55KW, this project is needed to use one set of unit (CB-V065).
Comparison of economic benefit estimation: the traditional air-conditioning input power (55KW cooling capacity) is at least about 21KW, and the CB-V065 input power per set is of 14.07KW. The energy saving is up to 33%. The annual saving is more than 13000 CNY. (According to 8 months per year, 30 days per month, 8 hours per day of operation, electricity by 1 CNY/1 degree calculation)